Knowing the sequence of operation for this type of starting relay can help you diagnose, confirm, or rule out certain service problems.
Potential starting relays consist of a high resistance coil and a set of normally closed contacts. The coil is wired between terminals 2 and 5, with the contacts between terminals 1 and 2.
Terminals 4 and 6 are used for capacitors and/or condenser fan connections and have no electrical significance to the starting relay itself, as shown in Figure 1. In fact, terminals 4 and 6 are sometimes referred to as “dummy” terminals and are simply used for wire connections.Figure 2 shows how a potential relay is wired to a capacitor-start/capacitor-run compressor motor. Notice that the relay coil is wired in parallel with the start winding and the start capacitor.
The run and start capacitors provide the phase shift for starting torque because their capacitances add up when wired in parallel. In fact, both capacitors are wired in series with the start winding and in parallel with the run winding.
The run capacitor limits the current that will pass through the start winding when the motor is running, because they are wired in series. The run capacitor also provides running torque when the motor is up and running.
The operation of the potential relay is based on the increase in back-electro-motive force (back-EMF) or a bucking voltage that is generated across the start winding as the motor increases in speed. The large metal mass of the motor’s rotor turning at high speeds with motor windings in close proximity has a voltage-generating effect.
The back-EMF voltage generated across the start winding causes a small current to flow in the start winding and potential relay coil, because they are in the same circuit. When the back-EMF has built up to a high enough value (referred to as pick-up voltage), the contacts between terminals 1 and 2 will be picked up (“opened”). This will take the start capacitor out of the circuit.
Pick-up voltage usually occurs when the motor has reached about three-fourths of its speed. The start winding is still in the back-EMF circuit, keeping the relay’s coil energized while the motor is running at full speed.
The contacts open because of the electromagnetic force (magnetism) generated in an iron core around which the relay’s coil is wrapped (Figure 3).
When the cycling control opens, line voltage is taken away from the motor. The motor’s rotor decreases in speed. Thus, the back-EMF generated across the start winding decreases in magnitude. The relay’s coil now sees a lower back-EMF and no longer can generate enough magnetism in its iron core to keep contacts 1 and 2 open.
The contacts therefore return to their normally closed position by spring power as the motor coasts to a stop.
With the start capacitor out of the circuit, the motor becomes a permanent split capacitance (PSC) motor in the running mode only.
Tomczyk is a professor of HVACR at Ferris State University, Big Rapids, MI, and the author of Troubleshooting and Servicing Modern Air Conditioning & Refrigeration Systems, published by ESCO Press. To order, call 800-726-9696. Tomczyk can be reached at email@example.com (e-mail).
Sponsored Content is a special paid section where industry companies provide high quality, objective, non-commercial content around topics of interest to the ACHR News audience. All Sponsored Content is supplied by the advertising company. Interested in participating in our Sponsored Content section? Contact your local rep.
24v Surge Protector Manufacturers Cheap Price
On Demand Refrigerant Safety Classes A2L and A3 have a very low GWP, making them a strong, long-term solution for many HVACR applications. However, these refrigerants are classified as mildly flammable and highly flammable respectively. This flammability class raises safety and compliance concerns. This webinar will help you understand these classes, along with the opportunities these refrigerants can offer.
As the HVAC market continues to expand and Variable Refrigerant Flow (VRF) technologies continue to evolve, the demand for contractors with VRF expertise will only grow. This presentation provides thorough insight into the requirements, advantages and opportunities associated with specifying VRF systems and addresses the common misconceptions contractors may encounter in the field.
In this issue of The NEWS, we present the Residential Heating Showcase, featuring the latest heating equipment to hit residential HVAC. We also discuss developments in the tools and test instruments market.
Universal circuit breaker, Molded case circuit breaker, Dual power - Shimin,https://www.shsminele.com/